4000W DC 24V/48V/96V AC 220V/230V off Grid Solar Inverter I-J-4000W-48V/96V-220V
|FOB Price:||US $400.58-426.55 / Piece|
|Min. Order:||1 Piece|
|Min. Order||FOB Price|
|1 Piece||US $400.58-426.55/ Piece|
|Payment Terms:||L/C, T/T, Western Union, Paypal, Money Gram|
- Solar on grid ,off grid,Hybrid Inverter 200W-6000W
- 50 Products
- Product Image
- Product Name
- FOB Price
- Payment Terms
- Product Package
- Product Attribute
- Product Table
- Model NO.: I-J-4000W-48V/96V-220V
- Phase: Single
- Certification: CE, ROHS, UL, ISO9001
- Type: DC/AC Inverters
- Circuit Topologies: Full-Bridge Type
- Model Number: I-J-4000W-12/24-220V
- Input Voltage: 12V/24V
- Warranty: 1 Year
- Low Battery Shut Down: 40±0.5V
- Weight: 3.2kg
- Trademark: EPever
- Specification: 7.5kg 16.535(lb)
- HS Code: 8537109090
- Nature of Source Flow: Passive inverter
- Output Power: >1000W
- Brand: Y-Solar
- Power Source: Solar Power
- Nature of Wave String: Sine Wave Inverter
- Output Type: Single
- Output Frequency: 50/60Hz
- Wave Form: Pure Sine Wave
- Plug: 50/60Hz
- Over Load Shut Down: 2400W Over 10 Seconds
- Transport Package: 507X249X116mm
- Origin: China
It adopts intelligent IC control of this series inverter ,also have perfect defensive function ( Overload protection,
over current protection, high temperature protection ,short circuit protection , the battery reverse connect protection,
battery over voltage and under voltage protection are included. At the same time with built fuses). It also with
working indicator and fault alarm functions. It takes import high quality double sizes PCB circuit and components
to produce high quality product with high-performances.
This inverter with pure sine wave output so that can be applied to any type AC loads. With beautiful shape and
also can be taken easily because of the small size. Please kindly check product features as below:
1. Unique front and back double soft start technology
2. Core of CUP and the pulse width control technology of SPWM.
3. Special constant power technology.
4. Technology Of prevent the reverse Diode
5. With USB charge interface
6. Quarantine of front and back level
7. Perfect powerful fault protection function (including the overload protection, over current protection, high temperature
protection, short circuit protection, the battery reverse connect protection, and it is also equipped with inbuilt fuse)
8. Battery protective function (Battery over-voltage under-voltage protection, overvoltage, under voltage recovery and related function)
9. Shock-protect function
10. AC pure sine wave output has no effect on the use lifetime of equipment
11.This inverter with Aluminum shell, surface of sandblasting anodic oxidation treatment, high hardness and prefect shape
The installation should be operated by a person with enough electrical theory knowledge or somebody who acquire practical experience.
1. Connection Steps:
1)Check if all the components are all included. Such as, enclose bags and use manual. At the same time inspect
whether battery voltage is accordance with the rated input voltage.
Enough current should be offered from the input battery voltage. Details calculate is that the output power /input voltage/0.85=output current
For example: load of 1000w, the output voltage is 12v, so the input current =1000/12/0.85=98 (Ampere).
Appropriate connection wires should be chosen according to the current rule that within 1 meter 8A/mm. 12mm
connect wires should be regarded as the 1000w inverter with input voltage 12v. Others must also match with each other.
2) The GND wire of inverter should be connected to ground firstly before using. Do not regarded zero wire as the ground connect line.
3) Close the power of inverter, ie, press down the button "OFF"
4) Confirm the positive and negative polarity of battery, high voltage is the positive and low one is negative
5) Pull out the inverter input terminal, red means positive polarity (+) and black refers to negative polarity (-).
6) Choosing the suitable black area line according to the first step and then connect to black wire of inverter input terminal and pull tight at last.
7)Choosing the suitable red area line according to the first step and then connect to red wire of inverter input terminal and pull tight at last.
8) Connect the black wire on the other side of the battery negative pole and ensure connection is firm.
9) Connect the red wire on the other side of the battery positive pole and make sure connection is firm.
10) Check and make sure all the connection are in right order and then the inverter power, just press the button "ON" is ok.
11) Inverter will get stable alternate current within 5 seconds after green led of inverter turn on.
12) The power of electronic equipment which connected to the AC socket of inverter shouldn't be exceed rated power of inverter.
13) Press the button "ON" and then the power switch of load will be opened.
2. Connection Diagram
|Model||DC input||Weight||AC output||Plug||Type||Frequency||Power|
|I-J-300W||12V or 24V||2||220V/230V||EU,AU||Pure Sine Wave|
Pure Sine Wave
Pure Sine Wave
|I-J-500W||12V or 24V||2||220V/230V||EU,AU||50/60Hz||500W|
|I-J-600W||12V or 24V||2||220V/230V||EU,AU||50/60Hz||600W|
|I-J-800W||12V or 24V||3.2||220V/230V||EU,AU||50/60Hz||800W|
|I-J-1000W||12V or 24V||3.2||220V/230V||EU,AU||50/60Hz||1000W|
|I-J-1500W||12V or 24V||4.8||220V/230V||EU,AU||50/60Hz||1500W|
|I-J-2000W||12V or 24V||5.2||220V/230V||EU,AU||50/60Hz||2000W|
|I-J-2500W||12V or 24V||10.8||220V/230V||EU,AU||50/60Hz||2500W|
|I-J-3000W||12V or 24V||10.8||220V/230V||EU,AU||50/60Hz||3000W|
|I-J-3500W||12V or 24V||13.6||220V/230V||EU,AU||50/60Hz||3500W|